@Ross_McCarthy, thanks for reply, finally someone who understand me
This should be the newest manual which I found:
Looking to 8.1.1 Energy buffering,
[C-07] needs to be
2 - therefore I bought Madoka for Heat Pumps, 2 weeks ago.
[C-07] = 0 or 1, Heating or cooling needs to be manually disabled.
and according to 2.3 System requirements
[4-08] = 1
[4-09] = 1
[E-05] = 1
[E-06] = 1
I am using Dry contact switch (SolarEdge) doing the same what you Plug/Socket do.
How I tested the Energy Meter: Set the pulse lenght to maximum and measure it with Voltmeter. The led pulses should corresponds with S0 pulses. It looks like that my Energy Meter is working sending the signals. I have played with 1000 and 100 pulses/kWh, lenghts from 10 to 500miliseconds, but nothing works reliable. Once or twice it was working for a while, but I cant repeat it.
Look what I have found recently:
2.4 On-site installation requirements
IF connection to an
electricity meter (X2A)
Electricity meter —
IF connection to a solar
Should I understand it as Alternatives?
It looks like that I can unplug the SG0, as Electricity Meter can do the Smart Grid controlling? I will try to unplug the SG0 signal tomorrow, hopefully it will be enough sun!
Question: with your X2M switch you mean an Home Automated switch like they have in ESPAltherma?
Question 2: What is your static power limitation in LAN Adapter web interface settings?